1. The configuration of fire extinguishers should be implemented in accordance with the "Code for Design of Building Fire Extinguishers Configuration", and the specific number should be calculated and determined according to the nature of the site, the layout of the site, the characteristics of danger, and the parameters of the extinguisher;
2. In general places, one 4kg dry powder fire extinguisher (ABC) shall be equipped for every 75 square meters, and no less than two at each point.
Indoor fire extinguisher configuration standard
1. The standard configuration of different buildings is the same.
2. Reason: According to the Announcement No. 97 of the Ministry of Housing and Urban-Rural Development of the People’s Republic of China on August 13, 2008, the "Code for Acceptance and Inspection of Building Fire Extinguishers" was approved and issued. This standard was formulated for the first time, and the standard number is GB50444-2008 , Implemented on November 1, 2008.
3. Building fire extinguisher standards:
(1) Water-based fire extinguishers (portable water-based fire extinguishers, trolley-type water-based fire extinguishers) maintenance period: 3 years after the expiration of the factory; every 1 year after the first maintenance; scrapped life: 6 years.
(2) Dry powder fire extinguishers (portable (storage type) dry powder fire extinguishers, portable (cylinder type) dry powder fire extinguishers, cart type (storage type) dry powder fire extinguishers, cart type (cylinder type) dry powder fire extinguishers) Maintenance period: 5 years after the expiration of the factory; scrapping period every 2 years after the first maintenance: 10 years.
(3) Clean gas fire extinguisher (portable clean gas fire extinguisher, cart-type clean gas fire extinguisher) maintenance period: 5 years after the expiration of the factory; scrapping period every 2 years after the first maintenance: 10 years.
(4) Maintenance period of carbon dioxide fire extinguishers (portable carbon dioxide fire extinguishers, cart-type carbon dioxide fire extinguishers): 5 years after the expiration of the factory; every 2 years after the first repair.
ZHEJIANG WINNER FIRE FIGHTING EQUIPMENT CO., LTD. is a leading China nonwoven manufacturers and spunlace nonwoven fabrics suppliers. Its product types include Fire Extinguisher, Gas Cylinder, Fire Extinguisher Accessory and peripheral configurations. If you want to learn more about Extinguisher related information, please visit ZHEJIANG WINNER FIRE FIGHTING EQUIPMENT CO., LTD.